|Place of Origin:||China|
|Minimum Order Quantity:||1 set|
|Packaging Details:||Inner Box, Carton, Pallet|
|Delivery Time:||4-8 days|
|Payment Terms:||L/C, T/T, Western Union,Paypal, MoneyGram|
|Supply Ability:||200000 sets per month|
|Product Name:||S Type TX 2 Thermostatic Expansion Valve||Inlet Port Size:||3/8'' Flare|
|Outlet Port Size:||1/2'' Flare||Refrigerants:||R22, R407C|
|Capillary Tube Length:||1500mm||Pressure Equalization:||Internally Equalized|
|Temperature Range:||-40°C To 10 °C||Direction:||Angleway|
|Connection & Body Material:||Brass||Application:||Freezing, Refrigeration And Air Conditioning System|
3/8'' x 1/2'' Flare R22 s Type 068Z3206 TX 2 THERM. EXP. Thermal Expansion Valve
The introduced following is s type TX 2 068Z3206 thermostatic expansion valve, 3/8'' x 1/2'' flare connection, R22 / R407C refrigerants, internally equalized, 1500mm capillary tube length.
Thermostatic expansion valves regulate the injection of refrigerant liquid into evaporators. Injection is controlled by the refrigerant superheat. Therefore the valves are especially suitable for liquid injection in dry evaporators where the superheat at the evaporator outlet is proportional to the evaporator load.
1. Large temperature range Equally applicable to freezing, refrigeration and air conditioning applications.
2. Rated capacities from 0.5 to 15.5 kW (0.15 to 4.5 TR) for R22.
3. Can be supplied with MOP (Max. Operating Pressure) Protects the compressor motor against excessive evaporating pressure during normal operation.
Main dimension of s Type 068Z3206 TX 2 Thermostatic Expansion Valve:
Technical data of s Type THERM. EXP. VALVE / Thermostatic Expansion Valve:
|Refrigerants||Model||Pressure equalization||Capillary tube length||Connection|
|R22||R22N-H||TX 2||Internally equalized||1500mm||3/8'' / 9.52||1/2'' / 12.7|
|R22W-H||TEX 2||Externally equalized||3/8'' / 9.52||1/2'' / 12.7||1/4'' / 6..35|
|R407C||R407CN-H||TZ 2||Internally equalized||3/8'' / 9.52||1/2'' / 12.7|
|R407CW-H||TEZ 2||Externally equalized||3/8'' / 9.52||1/2'' / 12.7||1/4'' / 6..35|
|R134a||R134aN-H||TN 2||Internally equalized||3/8'' / 9.52||1/2'' / 12.7|
|R134aW-H||TEN 2||Externally equalized||3/8'' / 9.52||1/2'' / 12.7||1/4'' / 6..35|
|R404A/R507||R404A/R507N-H||TS 2||Internally equalized||3/8'' / 9.52||1/2'' / 12.7|
|R404A/R507W-H||TES 2||Externally equalized||3/8'' / 9.52||1/2'' / 12.7||1/4'' / 6..35|
Details enlargement of TX 2 068Z3206 R22 3/8'' x 1/2'' Flare sType Expansion Valve:
Application examples of s Type TX 2 068Z3206 Thermostatic Expansion Valve:
Youtube video of s Type 068Z3206 TX 2 3/8'' x 1/2'' Flare R22 THERM. EXP. VALVE:
Selection and Installation Instructions of s Type Thermostatic Expansion Valves:
1. Select Valve Body
Select the valve body based on refrigerant and need for internal or external equalization using the table on the previous page under [Select Valve Body."
2. Select Orifice
T2/TE2 valve capacities are based on the installed orifice. To select the correct size orifice, use one of the two methods using the [Select Orifice" section on the previous page.
3) Assemble Valve and Install into System
1. Slide the orifice into the valve body and secure using liquid line flare nut
2. Attach evaporator inlet or distributor assembly to valve outlet flare nut
3. Tighten both flare nuts
4. Secure sensing bulb with enclosed bulb strap to suction line. Bulb should
be located between 1:00 and 4:00 on the tube, and the strap should be tight
enough that no bulb movement is possible.
5. Wrap included insulation tape beginning one inch before the bulb and overlapping each wrap, finishing one inch beyond the bulb on the other end.
4) Adjust Superheat
1. Remove the cap
2. Make superheat adjustments ¼ turn at a time (¼ turn ≈ 1.75 °F).
3. Reinstall the cap
Focus on your demands, Offer you best solution:
√ Contact us if some points you have doubt
√ Contact us if somewhere need to change
√ Contact us if not the one you are looking for
√ Contact us if you are doing designing
Welcome to your any question and inquiry!
Contact Person: Echo