|Place of Origin:||CHINA|
|Minimum Order Quantity:||1 pc|
|Delivery Time:||3 days|
|Payment Terms:||L/C, T/T, Western Union, MoneyGram|
|Supply Ability:||7777 sets per month|
|Port Size:||1 1/2 Inch||Type:||Direct Drive|
2S-400-40 Water Valve / Silver 1 1/2 Inch Stainless Steel Solenoid Valve Direct Drive
The two-position two-way water industrial valve uses high-quality copper core coils to enable the product to produce more stable magnetic properties and improve the stability of the switch.With 304 stainless steel valve body, it is strong and wear-resistant and does not rust.Thickened interface design for durability.
Voltage:AC220V AC110V DC24V
Body Material:304 Stainless Steel
Transfer method:Direct active
Port Size:1 1/2″
Oil seal material:NBR, EPDM
|Pipe size||1/8''||1/4''||3/8''||3/8''||1/2''||3/4''||1''||1 1/4''||1 1/2''||2''|
Note:Don't install the water intake and outlet in contrast
1. Special Note: The pipe must be cleaned and purged before installation to prevent impurities from clogging the valve port and destroying the sealing surface. If there are tiny impurities and dust, install a filter in front of the valve (filter ≥ 80 mesh cm2).
2. When installing, note that the arrow on the valve body should be consistent with the flow direction of the pipe, and the coil should be installed horizontally vertically.
3. Check whether the pressure, temperature and voltage are consistent with the actual parameters of the solenoid valve nameplate before installation.
4. Pay attention to the cleaning of the media. During the use, the components inside the valve should be cleaned regularly. After disassembly, the gasket should be inspected at the same time. If damage is found, it should be replaced in time.
5. When installing, clamp the valve body with a wrench, and then screw the pipe. Do not apply force to the coil to avoid bending and deformation of the solenoid valve and loosening of the connection.
6. After the solenoid valve is installed, it must be fluidly operated several times to ensure normal operation before it can be put into normal use.
Solenoid valve failure and elimination
|Does not work after power on||Poor contact of power supply wiring||reconnect|
|The power supply voltage is not in the working range||Adjust the normal position range|
|Coil short circuit||Replace the coil|
|Solenoid valve cannot be closed||Seal damage||Replace the seal|
|Fluid temperature is too high||Replace the solenoid valve of the opposite port|
|Impurities enter the solenoid valve moving iron core||Cleaning|
please care the products details at our website, any confuse please contact us or Note your request online. Big quantity purchase ,please contact our online service to ask more economic shipping way or discuss the more pretty price.
Wait your inquiry!
Contact Person: Decade